Monday, 29 September 2014
Predicting the Future of Densities
Nostradamus couldn’t predict the future and neither can we – which is why the data centre industry has never predicted future rack densities correctly
Just recently, there was yet another report generated predicting that data centres within the next few years will be running at 30, 40, or 50 kW per rack. I remember a conversation with someone (who shall remain nameless to protect the innocent) a few years ago and he insisted that we were only a few years away from 250kW in a single rack. I asked him if he ever considered what the power distribution system for that solution would look like….of course he hadn’t. The practical reality of the space and size of the supporting power distribution system alone (and we didn’t discuss the cooling complexity) would overwhelm the rack. So I asked him – why would you bother? I didn’t get an answer…
And he hasn’t been alone in these predictions. For years we have seen industry analysts…yes the experts in predicting the future….who have generated these same reports. And they have always been wrong. All the evidence I see today, and my own experience, is that data centers are running in the 3-5 kW per rack range which is up from 10 years ago when they were 1-2kW. We clearly have not seen the increase that all the prognosticators have predicted.
So I asked myself what is the correct density per rack? What are the trades-offs and is there some reason that the industry has stayed at relatively low rack density levels?
The result of this analysis is WhitePaper #156 – Choosing the Optimal Data Center Power Density.
Our findings are fairly straightforward:
1) When you analyse the cost of power and cooling infrastructure, there are significant economic advantages to achieving 5kW per rack on average. There continues to be some savings up to 15kW per rack, and there are effectively no savings beyond that level.
2) Most of the prognostications look at server power consumption numbers and don’t account for networking and storage racks which have a different load profile. When you count these the average comes down.
3) Most people overestimate the actual power consumption of servers due to nameplate ratings.
Like most people, I also can’t resist playing Nostradamus and trying to predict what will happen. My view is that the economics of a 5-15kW sweet spot is a natural market force to keep densities below 15kW. I’ve talked to some data centre operators today who won’t fully populate racks in order to stay under a 10kW limit – yes they purposely leave U space empty.
Additionally, there is also a reinforcing trend coming from Intel with performance per watt on chips. The focus seems to be driving toward reducing or at least maintaining power consumption while driving performance higher. Perform a cursory analysis of the performance per watt of an Atom chip and one can see some of the strides they are making. If I was a betting man, I would bet that this development / technology on low end mobile chips will migrate its way to higher end chips….and drive densities down.
And then we also found a web page giving analysis showing power consumption per U http://datacenterpulse.org/blogs/jan.wiersma/where_rack_density_trend_going
….so maybe we have been driving to lower density per rack all along?
I don’t deny that there are applications like HPC which may require higher densities for IT performance reasons. However, in most cases, I would argue that data centre operators should look closely and perhaps even enforce a policy limiting the densities they will allow in their data centre.
So I am not Nostradamus and from what I can tell he wasn’t very good at predicting the future either. (Check out this link if you are bored). However, I think there are some compelling arguments in favor of lower than projected densities.
And if you believe this, there are some practical (and I think quite fascinating) implications on how data center designs and specifications can be simplified….more to come on this topic in future blogs…
Guest blog by Kevin Brown, VP Global Data Center Strategy and Technology, IT Business, Schneider Electric, United States